Submitted by dortor on 02. März 2013
in the HPWC charger there are dip switches to configure the charger to know the size of the breaker it's wired to.
Question is related to the 80% rule (40 amp breaker only use 32 amps of continuous load).
Do you set the dip-switches in the HPWC to match the breaker, or the draw?
i.e. if I have a 60 amp breaker - would I set the HPWC dip switches to the 50 amp setting or the 60 amp setting?